Please suggest a solution. You could manually extract the data from the UIP file, but you would have to match the program segment parameters to their respective MODBUS registers note that they may change between versions of , then write those values directly into the device. Message 8 of The error explanation I get is:. Message 2 of
|Date Added:||21 February 2013|
|File Size:||56.57 Mb|
|Operating Systems:||Windows NT/2000/XP/2003/2003/7/8/10 MacOS 10/X|
|Price:||Free* [*Free Regsitration Required]|
As for the ethernet cards, there are have been two on the computer we’re using from the start. Overview Topics Products People Change log.
Message 4 of Hi MatthieuMag, To be able to debug what is the root cause of your timeout error 56 problem, could you post your code or a sample of it? Community-powered support for Eurotherm. Create a new topic About this Question 8. The PLC ping normally on the prompt I’m not too familiar with neither the modbus protocols nor the API though I’ve read quite a bit about it since I’ve had to setup communication with that eurotherm.
Help get this topic noticed by sharing it on Twitter, Facebook, or email. I already configured the micrologix to talk through the ethernet port, but, how can I test the comunication? But in the main program, now there is a new error that arises at the et Configure Instrument Mode.
Did you know that your browser is out of date?
However, i labviw not able to communicate with with my itools or labview. I have attached an example file for testing, the vi request the current PV register address 1 from the eurotherm.
In the picture is how I wired them up with the screw terminals. Hope that helps, Adrian.
how can I program Eurotherm program sagments using LabView
Auto-suggest helps you quickly narrow down your search results by suggesting possible matches as you type. Message 2 of Hi friends, anyone already used micrologix with this library?
You could manually extract the data from the UIP file, but you would have to match the program segment parameters to their respective MODBUS registers note that they may change between versions ofthen write those values directly into the device. You might need to refer the manual.
Eurotherm temperature controller
Message of You should not delete the property nodes, rather you should have replaced with some other code which is relavant to ethernet communication. This might help to corner the issue. Humberto Souza February 16, Thank you, I am able to match it up with the code on the user guide. How should I communicate with ?
Acknowledged In progress Doesn’t need answer Answered. I’m a bit confused as to how to troubleshoot this setup. This section contains tables with all the information you need, labvuew modbus addresses and offsets.
Did you solve your problem? Dig into the Initialize. I am attaching the other. Power cycling the device has no effect – I’ll get 3 good readings, then an error, then 2 good readings, then another error.